Miracle cooperated with a refrigeration solenoid valve factory that has 28 years of experience in designing, manufacturing, and marketing solenoid valves.
We provide CE, UL, CQC, ISO9001, and ISO1400 certificates for the solenoid valve.
As the solenoid valve supplier, miracle provides different types of solenoid valve to meet your requirements, also provide customized solenoid valve for your special requests.
EVR Solenoid valve
EVR solenoid valve is a one-time opening or two-time opening valve, it is suitable for one-way flow.
⦁ EVR solenoid valve has a wide application, such as liquid, suction, and hot gas pipeline in freezing, refrigeration, and air conditioning equipment.
⦁ The solenoid valve seat has a very reliable sealing.
⦁ We can provide various voltages for the solenoid valve coil, to meet your demand for different markets and applications.
⦁ We do not only supply the complete solenoid valve but also provide the separate solenoid valve body and solenoid valve coil.
Applicable refrigerants:HCFC, HFC.
Ambient temperature: -40℃~+65℃.
Normal open and normal close type is available.
Standard Voltage: AC 220V/50Hz, AC110V/50HZ, AC110V/60HZ,24V/50HZ,12V/50HZ, etc.
We can also customize for you, Just tell us the voltage and frequency you need when placing the order.
Allowable voltage fluctuation of coil:+10%~15%.
Max working pressure: 3.5MPA.
Coil waterproof level: IP65.
Check the following technical data to choose the suitable refrigeration solenoid valve for your system.
The Working Principle of Refrigeration Solenoid Valve
One-time opening type(Direct-acting type)
EVR3 is the direct-acting type solenoid valve.
When the stainless steel core part moves up because of the magnetic force from the solenoid valve coil, the refrigeration solenoid valve opens directly.
It means the solenoid valve is able to work under the zero pressure difference.
The sealing core is installed on the stainless steel core, the inlet pressure is on the stainless steel core part.
So when there is no electricity for the coil, the inlet pressure, spring force, and stainless steel core weight work together to close the valve.
Two-time opening(Servo Type)
EVR6/10/15/20 is the servo-type solenoid valve with the movable valve core part.
The pilot valve core and the diaphragm are on the valve core parts.
When the refrigeration solenoid valve coil is not be charged with electricity, the main valve port and pilot vale port are all closed.
The weight for the stainless steel valve core part, the spring force, and inlet&outlet pressure difference work together to make the valve closed.
When the coil is charged with electricity, the stainless steel valve core moves up.
Because it is forced by the magnetic, then open the pilot valve on the diaphragm.
By then, the pressure on the diaphragm is decreased, the top of the diaphragm is connected to the inlet of the solenoid valve.
The pressure difference for the inlet and outlet of the solenoid valve makes the diaphragm moves up and open.
Therefore, the valve should be open and there must exist a minimum pressure difference;
When the coil lost electricity, the pilot valve is closed, the pressure on the diaphragm is increased the same with inlet pressure through the balance hole of the diaphragm.
Make sure the diaphragm moves down and closes the main valve port.
Unloading Solenoid Valve
The unloading solenoid valve is a type of solenoid valve that can be loaded by itself according to the heat load reducing situation.
It will save energy for the compressor and it has a longer working life.
It is widely used for freezing, refrigeration, and air conditioning equipment.
It is also can be supplied for a complete solenoid valve and separate valve body and valve coil.
This type has normally open and normal close to choose from.
There are many types of AC and DC voltage and frequency for the valve coil to choose from.
It suits HCFC, HFC refrigerants.
Working pressure difference: 0-21bar.
Max working pressure: 30bar.
Applicable temperature: -25℃-105℃.
R410 Solenoid Valve
R410 solenoid valve is a new type of solenoid valve that is specially designed for R410 refrigerants, of course, it is also applied for common refrigerants.
It has the same application as the above refrigerant solenoid valve, poplar for the liquid pipeline, suction pipeline, hot gas pipeline for refrigeration system, air conditioning system.
Applicable media temperature:-40℃-105℃.
Max temperature when defrosting:+130℃.
Ambient temperature: -40℃~+55℃.
Max working pressure:45BAR.
Solenoid valve coil: AC and DC,50hz, or 60hz are all available.
For detailed specifications, please kindly check the attached sheet.
Castel Solenoid Valve
Castel solenoid valve is a type of diaphragm solenoid valve, as an automatic control part in the refrigeration system, it uses to control the pass or stop of refrigerants.
It is popular in refrigeration compressor condensing units, central air conditioning, bus air conditioning, and other freezing or cold storage system.
If you are using the Castel brand solenoid valve, we welcome you to try our valves that have the same function, equal quality but better price.
It will increase your competitiveness for these valves in your market.
Applicable media Temperature:-35℃-105℃
Max/Min opening pressure: 2.5MPA/0.05MPA
Working pressure:3 MPA
Service Life:100,000 cycles
Standard Size: 1/4 Inch to 1 5/8 Inch for connection
As the Castel solenoid valve supplier, we can customize for your special requests, contact us for details.
Solenoid Valve Coil
The solenoid valve coil is the indispensable accessory for the refrigeration solenoid valve.
Only with the coil, the solenoid valve can work normally. And the coil only can be charged with electricity when installed on the valve, or it will be damaged.
We have many voltages and frequencies for different applications and different markets.
Such as AC220v,110v,208/230v etc are normally use for commercial refrigeration and AC system,also supply DC12v,24v use for transportation refrigeration system.
We have a type and b type for different solenoid valves, the applicable ambient temperature is -25℃~+80℃, allowable voltage fluctuation is +10% to -15%.
The following technical sheet will help you to know them better and choose the most suitable coil for your system.
Solenoid Valve in Refrigeration System
In the refrigeration system, each valve needs to cooperate well with each others.
So it can ensure the normal and complete operation of the whole system.
Notes the following important using instructions to make sure the long life running of the refrigeration solenoid valve and system.
All the refrigeration solenoid valve has to be installed correctly according to the flow direction(there will be an arrow to point the direction on the valve), then it will work smoothly.
For the refrigerant solenoid valve that needs to be installed before the expansion valve in the system, make sure to install it near the expansion valve, this will avoid the liquid hitting situation when open the refrigeration solenoid valve.
Ensure the pipeline around the solenoid valve is installed and connected very well, to prevent the rupture problem.
You need to take some suitable measures to prevent heating damage for the refrigeration solenoid valve when you do the welding work.
Test the pressure of the refrigeration system
When you test the pressure of the system, you have to energize the coil or open all the solenoid valves in the system manually(If there is a manual operating lever is installed).
Screw back the operating lever before you start the system, otherwise, the refrigeration solenoid valve will not be able to close.
Finally, when you fix the refrigeration solenoid valve to the pipeline.
You must use the reaction force as always, which means you need to use two wrenches to tighten the solenoid valve on both sides.
Installation of the solenoid valve coil.
When you install the valve coil to the refrigeration solenoid valve.
You need to install an o-ring between the valve body and coil, align the coil hole with the connecting steel, press the valve coil until you heard the closing sound, which means you install the coil in the right place.
Maintenance for refrigeration solenoid valve
When you do the maintenance, please change the o-ring.
When you install the coil to the valve body during repairing.
Please pay attention to the inlet of the cable, the cable has to lead out through a drip bend, must make sure no water enters into the solenoid valve coil cable.
Make sure the o-ring is smooth, with no damage and no paint or other objects on the surface.
Choose the right and most suitable solenoid valve for your system.
Choose the right cable, please always use round cable because it’s the type of cable that has an excellent sealing function.
It has been tested by actual work and turns out it has an effective sealing.
Make sure the voltage and frequency of the solenoid valve coil are right for your system, or it doesn’t match, the coil will be burnt.
For some refrigeration systems, it requires the refrigerant solenoid valve to remain close during the working conditions, you need to use the normal close type solenoid.
Of course, for some systems that need the refrigeration solenoid valve to remain open during the working conditions, choose the normally open type refrigerant solenoid valve.
And they can not be replaced in these situations.
Our aim is to do more and make your business easier and more profitable.
For achieving that, we are on the way to strengthening ourselves day by day, step by step.
For now, we have got CE certificates, UL certificates, ISO quality control systems, CQC certificates to improve our product quality level, safety level, and service level, and can fulfill customers’ demands from different markets.
We devoted ourselves to arranging everything you need well and providing you with the most convenient way for business.
Common Failure and Treatment Methods of Solenoid Valve
The refrigeration solenoid valve doesn’t work after energizing.
A: The wire is not connected well, and it can’t provide the power supply.
B: The medium pressure or working pressure difference is not matched.
C: There are some impurities to stuck the solenoid valve core.
A: Re-connect the wire.
B: Change a new refrigeration solenoid valve that matches the working pressure difference well.
C: Clean the valve, change the sealing part if it’s damaged, and install the filter drier before the refrigeration solenoid valve.
The refrigeration solenoid valve can’t be closed.
A: The spring inside is deformed or has expired.
B: The valve core or the sealing ring is worn.
C: There are impurities entering into the valve core.
D: The sealing gasket is dropped, damaged, or deformed.
E: The balance hole or the orifice is blocked.
A: Change a new spring for the refrigeration solenoid valve.
B: Replace the refrigeration solenoid valve.
C: Clean the refrigeration solenoid valve.
D: Replace or reassemble the refrigeration solenoid valve.
E: Clean the refrigeration solenoid valve regularly.
The leakage of the refrigeration solenoid valve.
A: The connection of the refrigeration solenoid valve is loose.
B: The sealing part of the refrigeration solenoid valve is damaged.
A: Tighten the bolt or the connecting thread.
B: Change a new sealing part.
Internal leakage of the refrigeration solenoid valve.
A: The main valve and pilot valve are not matched well or have already deformed.
B: The spring didn’t assemble well or was deformed.
A: Change a new sealing gasket.
B: Change a new spring.
Heavy noise when the refrigeration solenoid valve is working.
A: The fasteners are loosened.
B: The medium pressure or viscosity is not matched with the system.
C: The fluctuation of the voltage is out of the allowable range.
A: Tighten it again.
B: Change a new and suitable refrigeration solenoid valve.
C: Adjust the voltage.
The solenoid valve does not change direction, and the heating and cooling for AC cannot be interchanged.
The power supply voltage is lower than the rated voltage of the refrigeration solenoid valve, the pressure difference of inlet and outlet is over the ability to open the valve, this cause the valve core can’t attract and close.
Improve the power supply.
Miracle is the refrigeration parts supplier.
No matter you are doing refrigeration projects, or sell the parts as a wholesaler, or you have shops, we all have a solution for you.
Just contact us for professional suggestion and starts your business in an easier way.