Your Top Hot Gas Bypass Valve Supplier
The hot gas bypass valve is also called hot gas solenoid valve. It only needs to add a solenoid to the bypass valve control system.
As a reliable refrigeration supplier, Miracle can provide you with multiple types of hot gas bypass, such as Sporlan type bypass valve, Danfoss type bypass valve, Parker type bypass valve, etc. For more details, please contact us now.
CBX series hot gas bypass valve is made of high-quality brass, with mature production technology and stable quality. This bypass valve is designed for welding, and the maximum working pressure is 28Bar. Send your request today.
The hot gas bypass valve is generally installed at the exhaust port of the refrigeration compressor. With a reasonable design, it can effectively prevent the evaporator from freezing and reduce the risk of ice blockage. Miracle hot gas bypass valve can be applied to various refrigerants such as R134a and R410. For more product details, please contact us now.
Danfoss hot gas bypass valve is an original Danfoss product, with a maximum test pressure of 31 bar and a maximum working pressure of 28 bar. The applicable temperature range is -50℃-140℃, the connection method is ODF, and the refrigerant has a wide range of applications, such as R448A, R449A, R507A, R513A, R600, R600a, etc. For more details, please contact us now.
- Quality Assurance
- One Stop Shopping
Miracle devoted ourselves to doing our best to make your business simple and profitable, so we never stop our effort to improve our hot gas bypass valve quality and service.
So now we have ISO9001 certification, CE certification, UL certification, and CB certification to ensure good and reliable product quality hope to use our passion and expertise to make your business competitive with our products!
As a reliable refrigeration wholesaler in China, Miracle has stricter control over the quality of hot gas bypass valves.
On the one hand, we actively promote R&D and improvement to provide you with a richer variety of hot gas bypass valves.
On the other hand, it also extends the product warranty time, making your purchase more worry-free. Contact us now.
Whether you have HVAC or refrigeration needs, Miracle all can meet your purchasing needs.
We provide you with high-quality accessories that match the hot gas bypass valve, such as refrigerant sight glass, 4-way reversing valve, refrigeration ball valves, air conditioner valve, HVAC valve, etc.
What is Hot Gas Bypass Valve
The hot gas bypass valve is an energy adjustment device.
It will bypass the high-pressure side gas to the low-pressure side.
That means the high-temperature gas refrigerant on the high-pressure side bypasses the low-pressure side of the system.
To ensure the system can operate very well under the condition of given minimum return pressure.
A hot gas bypass valve is no variable device for the compressor.
The hot gas bypass valve provides a useful, economical, and reliable energy regulation solution.
When the load drops, the suction pressure drops to a certain level, the suction pressure drops below the low-pressure control value.
Even when the pressure is at such a low load if you still don’t want to stop the system and require it to work normally.
Then you can use the hot gas bypass valve to adjust the energy.
The units that adopt the hot gas bypass valve is on the condition of low load.
It can effectively limit the evaporation pressure and prevent the system from switching on and off, ensuring the compressor runs well under the designed return gas pressure, maintaining better echo oil performance.
And also effectively preventing the evaporator coil from frosting.
How to Install a Hot Gas Bypass Valve
Method 1: Bypass the hot air to the suction pipe of the compressor
A hot gas bypass valve leads some hot gas from the exhaust pipe of the compressor to the suction pipe of the compressor.
When the hot gas enters, the suction temperature increases and the exhaust temperature will increase inevitably, then the gas temperature between the exhaust valve port and gas return port will drop around 10℃-23.9℃.
If the bypass flux is too much, the exhaust temperature rises too much, it will exceed the maximum allowable exhaust temperature and damage the compressor.
For avoiding that situation, the system needs to use a liquid injection valve to lead some liquid refrigerant from a high-pressure liquid pipeline to the suction pipeline.
When the liquid refrigerant evaporates, it will absorb the heat and release cool, then it can control the excessive rise of the exhaust temperature.
With this kind of arrangement method, the load is too low to a certain level, the flow rate of the refrigerant in the evaporator is too slow, which will cause difficulty in oil return.
Therefore, you can use the method to bypass the hot air to the middle of the front of the evaporator.
Method 2: Bypass the hot air to the inlet of the evaporator
Using this method, just like the hot gas provides an additional load for the evaporator.
The evaporator can be used as a direct mixing chamber, although the actual load is low, the expansion valve still can control much liquid supply for the evaporator, ensuring enough refrigerant flow speed inside of the evaporator.
The oil return function is greatly improved, even no more extra parts are added during the system, it can also avoid any other difficulties.
This arrangement method can defrost the evaporator when used in the air conditioning system.
The hot gas bypasses the inlet of the evaporator, even if under the condition of the evaporator is lower than the compressor.
When the system is under a low load, bypassing the hot air to the evaporator can make sure the proper oil return to the system.
When the hot gas is bypassed to the inlet of the evaporator, the hot gas bypass valve should be as close as possible to the compressor, to avoid the condensing of the hot gas bypass valve.
How to Adjust Hot Gas Bypass Valve
The main function of the hot gas bypass valve is to prevent the suction pressure is too low, even lower than the expected setting pressure value.
Then it can balance the cooling capacity in the refrigeration system.
So the first step after the installation of the hot gas bypass valve is to determine the lowest suction pressure under the operating condition, use it as the set point of the hot gas bypass valve.
Start the system and check whether the system works well.
Install a pressure gauge on the suction pipe of the compressor and measure the suction pressure after the system is stable.
For ensuring no hot gas bypassing at that time, please listen to the sound to see if there is air flowing inside of the hot gas bypass valve, or touch the outlet of the hot gas bypass valve.
If the temperature is too high if there is a sound inside of the hot gas bypass valve, which means the hot air has been bypassed already.
For preventing the hot gas bypass, you can cut off the power supply of the solenoid valve in the hot gas bypass line.
Or adjust the adjusting lever to make sure the hot gas bypass valve is in the closing condition.
Reduce the evaporator load until the suction pressure drops to the set point that the hot gas bypass valve requires.
You can choose the following way to reduce the load of the evaporator:
Close the outlet of gas, cover the evaporator, reduce the airflow, turn off the fan, turn off the bypass water of the water cooler.
Make sure the solenoid valve on the hot gas bypass line is open at this time.
Adjust the adjusting rod of the hot gas bypass valve, let the hot gas bypass valve begin to bypass the hot gas until the suction pressure no longer drops, and remain at the excepted value.
Change the load of the evaporator again, test whether the suction pressure under different working conditions is lower than the set pressure value.
Replace the sealing cap on the adjusting rod of the hot gas bypass valve.
Hot Gas Bypass Valve Using Tips
Do not use the refrigerants with the unknown using condition or is not on the list.
When you install the hot gas bypass valve, ensure the flow direction of the refrigerant is in the same direction as the arrow direction on the hot gas bypass valve.
In order to protect the internal parts of the hot gas bypass valve from moisture and impurities.
We will recommend you install a filter drier before the hot gas bypass valve in the refrigeration system.
Please wrap the hot gas bypass valve body with a wet towel when welding, this can avoid the damage of internal parts of the hot gas bypass valve because of the overheating for the hot gas bypass valve body.
For the parallel unit system, the hot gas bypass flux can’t be higher than the cooling capacity of a single evaporator.
It is necessary to use multiple hot gas bypass valves to control the system.
If the compressor is located in the front of the evaporator.
When the hot gas bypasses the evaporator, it has to make sure enough oil is returned for the compressor under the low load working condition.
When the hot gas bypass is installed in the evaporator.
It is necessary to insulate the hot gas bypass piping if the bypass piping is too long.
For the refrigeration system with a capillary tube, do not use hot gas bypass valve.
For the refrigeration system with an automatic expansion valve, do not use hot gas bypass valve.
For the system with non-adjustable super-heat expansion valves, do not use hot gas bypass valve.
Why Choose Miracle Hot Gas Bypass Valve
The hot gas bypass valve factory that Miracle cooperated with is designing, manufacturing, and selling hot gas bypass valves in the domestic market and the overseas market for 20 years.
We provide CE, UL, ISO9001, and CB certifications for a hot gas bypass valve to support your business.
- Excellent design with a small corner, very easy for installation.
- It has an accurate pressure regulation.
- Welding connection, the standard size is Inletφ8*1, outlet:φ10*1.
- The adjustment pressure range is 0-0.7Mpa.
- It is suitable for all the common refrigerants, like R134, R22, R502, etc.
- Safety working pressure is 2.8Mpa.
- SAE and ODF connections are all available.
Hot Gas Bypass Valve TQC
With more than 20 years of experience, Miracle is always treating quality as our factory life.
So we have a very strict inspection system for every refrigeration valve that comes from our factory.
√ Firstly, inspection is for the raw material, like copper pipe, stainless steel, brass, also includes the small parts even for the screw, gasket, we have specific requirements for our supplier.
√ Secondly, every product has strict production instructions, especially for the processing procedure and testing procedure.
After that, we also have a specific inspection department to test all the ready products already before delivery.
√ Thirdly, the responsible sales manager will inspect each item before delivery.
They will take a pic, measure sizes, and other data is important, even bring the drawing if it has.
√ Last but not the least, we will guarantee the quality of all the products from our factory and will be responsible for them.
So you don’t need to worry about the after-sales service at all.
Any problem, just contact us directly, we are always here for you.
Hot Gas Bypass Valve Mode of Transport
For ensuring a good delivery time and catch your business schedule, we will choose the forwarder who has a good and reliable service for transport.
Now we provide the shipment by sea, by air, by railway from any of the ports of China, if you need, we can also provide door to door service.
Also for sample or trial orders in small quantities, we also use international express, like DHL, FedEx, Ups, etc.
The freight forwarding companies we are cooperated with are the leading forwarder in China.
We all have more than 10 years of experience and cooperated with more than 500 companies by their expert service, fast response, competitive shipping costs, and good service.
We have a strong business ability for clearance and delivery worldwide.
We will make sure to provide you with the most economic shipment method and let you get the goods with the shortest time, lowest price, and most simple procedure.
Hot Gas Bypass Valve Related Products
Miracle is the supplier for complete solutions of refrigeration parts and refrigeration equipment.
So we can serve you very well, no matter you are a factory, you are project provider, contractor, or wholesaler, retailer, we all have a suitable solution for you.
So except for the hot gas bypass valve, we also have a refrigeration oil separator, filter drier, suction accumulator, access valves, liquid receiver, expansion valve, solenoid valve, 4-way reversing valve, refrigeration check valve, refrigerant shut-off valve, and others.
And we also provide the equipment for cold room, air conditioning system.
Such as condensing units, refrigeration units, evaporators, evaporator coil, and condensers. Contact us for detailed information and professional solution.